Transformer Oil Purification Plant CMM-1.0
Figure 1 – CMM-1 general view (doors are not shown for convenience)
|1||Maximum capacity, m3/h: – drying and filtration mode – filtration mode||
|2||Maximum oil output temperature in heating mode, °С||
|3*||Treated oil parameters (at initial moisture content of no more than 50g/t): – maximum moisture content by weight , gram per ton – filtration fineness, mcm||
|4||Oil feeding height relative to outlet fitting, m||
|5||Input pressure, MPa, no less than||
|6||Oil heater power, kW,||
|7||Oil heater mean surface power, kW/cm2, no more than||
|8||Rated power consumption, kW||
|9||Three-phase VAG @ 50 Hz, V||
|10||Maximum dimensions, mm – length – width – height||
|11||Maximum weight, kg||
- moisture content by weight – no more than 0,005% (50g/t)
- oil heating temperature up to +60±5 ºС within 30 minutes of heating;
- gas content – no more than 10%
Figure 2 – Cartridge filter: 1 – oil input line; 2 – filtered oil output line; 3 – contaminant drain valve; 4 – filter element; 5 – air vent plug; 6 – magnets; 7 – clamp It consists of a cover and a case, where filter elements of EFMG type are installed. The cover is equipped with a plug for air outlet, when the filter is filled with oil and for air inlet in case of oil draining of the filter. In the bottom of the filter it is designed a manifold with a valve. Oil input and output lines are welded to the case. Vacuum column CV (figure 6) is designed for heating and drying of transformer oil. General view of the vacuum column is shown in figure 3.
Figure 3 – Vacuum column: 1 –body; 2 – viewing window; 3 –cover; 4 –filter-activator (sprinkler); 5 –indicator of level; 6 – pipe connecting to a vacuum system; 7– inlet air pipe; 8 – oil inlet pipe; 9 – oil outlet for processed oil; 10 –lower level sensor; 11 –top level sensor
OIL HEATEROil heater is a thermally insulated cylindrical container with electric heaters inside (12 pieces electric heaters with power of 1.2 kW). To prevent overheating, there is a sensor for measuring and regulation of temperature on outlet of the heater.
CONTROL BOXThe control cabinet is designed for placement of the electric equipment required for regulation of the unit operation. It is a metal cabinet with lockable door. The inner panel contains electrical switching equipment. The panel contains control buttons and light indication devices. Figure 4 shows general view of control cabinet front panel, which contains:
Figure 4 General view of control cabinet panelControl and measurement devices The unit operation is controlled via the following control and measurement devices:
- measuring regulator shows treating oil temperature at the output of oil heating block of vacuum column;
- pressure gauges M1-M2 show contamination of filter elements in cartridge filters F1 and F2;
- vacuum gauge В is used for control of vacuum value;
- light indication on the CCU front panel shows whether heating elements TEH are switched on/off.
- Filtration with pre-heating and thermo-vacuum purification.
GlobeCore OIL PURIFICATION PLANT TYPE CMM-1.0