Transformer Oil Purification Plant CMM 1/6
- Removal of Water from 100 ppm down to 10 ppm and from 50 ppm to 5 ppm in a single pass and down to 3 ppm after 3 passes (ASTM method D-1533).
- Reduction of Gas content from fully saturated with air (10 to 12% by volume) to less than 0.1 % (ASTM D-2945).
- Removal of Particulate Matter to 1 microns
- Improvement in dielectric strength up to 80 kV
VACUUM SYSTEMCMM 1 /6 will have the following vacuum facilities:
- GlobeCore Rotary Vane Positive Displacement Pump
- Globe Core Vacuum Booster
VACUUM CHAMBERThis Oil Purification plant will have horizontal Vacuum Column with Coalescers. Vacuum Chamber Vessels and all internal parts are made of carbon steel and feature Coalescers, Sight Glass, Oil Level Controller and Vacuum Gauge. Vacuum Chamber’s rigid design makes it suitable for stationary and mobile installation. Appropriate flexible connections are provided to the outlet pump and inlet pump to minimize negative effect of vibration during plant operation and transportation.
Vacuum Chamber: 1–Oil Inlet; 2–Vacuum Pump Connection; 3–Coalescers; 4–Oil Outlet; 5–Level Sensor; 6–Sight Glass Coalescers – four built-in coalescers are provided for the maximum exposure of oil to the effect of vacuum. Due to reduced pressure dissolved water and gases are vaporised through secondary chamber and filter into atmosphere. Secondary Chamber (Oil Trap) – serves as safety feature to ensure that no oil is pulled into the vacuum pump. It is equipped with oil level sensor which will activate the alarm in case of oil presence. Oil Level Controller – consists of three capacitive probes provided to maintain required level of oil in the Vacuum Chamber. Vacuum Gauge – is provided to monitor Vacuum level in the Vacuum Chamber. Vacuum gauge will be absolute type with display in mbar. Vacuum ports – vacuum connection is provided to pull vacuum on transformer. Sampling Ports – inlet and outlet oil ports are provided for incoming and processed oil.
OIL HEATERThe electric oil heating facility will be provided in 2 stages offering a total of 55 kW of power. A low watt density encapsulated heating elements (1.2 W/cm²) are used to prevent heat degradation of oil. The Heater is controlled by electronic temperature controller.
Oil Heater: 1–Vessel; 2–Heater’s cover; 3–Heating Elements; 4–Oil Outlet; 5–Oil Inlet; 6–Drainage and Safety Valve; 7–Thermal Converters
- INLET AND OUTLET OIL PUMPS
A 90 micron Mesh Strainer is provided to remove large particles that could cause damage to the Inlet Pump. 25 micron Coarse Filter is installed on entry to the Vacuum Chamber. Oil receives its final treatment by passing through the 5 micron Fine Filter designed to remove 99.9% of particles larger than 5 microns.
Coarse and fine Filters: 1–Oil Inlet; 2–Oil Outlet; 3–Drain Valve; 4–Air Valve; 5–Manual Air Discharge; 6–Magnets; 7–Clamp; 8–Filter Cartridge
ALARMS AND INTERLOCKSGlobeCore’s CMM plants feature the following safety devises which ensure simple and reliable operation and will safely shut down the system in case of any alarm situation: High Level Alarm – will alert plant’s operator by activating sound and light alarms and shut down the system safely should high level of oil persist. Low Level Alarm – interlocked with the inlet pump low level alarm will safely shut down the plant in case of insufficient oil level. Flow Sensor – only activates the Heater when oil flow is detected. Overloads – all motors are protected by overloads. Alarms – sound and light alarm with silence button will alert plant’s operator of any emergency situations. Foam Sensor – prevents excessive foaming.
INSTRUMENTATION AND CONTROLSControl panel is a dust proof enclosure (protection class IP 54) featuring the following elements: 1–Power “on” and “off” switch; 2–PLC; 3–Power indicator «Power»; 4–Emergency «STOP» button 5–Indicating lamp of correct phase connection «Phase control»; 6–Power “On” indicator; 7–Manual control switch for vacuum pumps «VP1/VP2»; 8–Control switch of oil pumps «P1», «P2»; 9–Control switch of heating elements «Heating I», «Heating II»; 10– Manometers for monitoring state of Coarse and Fine filters and oil pressure on inlet and outlet
Plants automated operation will be controlled by Mitsubishi Alpha 2 Programmable Logic Controller.
Typical Flow Diagram CMM-1/6: СV – Vacuum Chamber; P1 – P2 – Oil Pumps; K1 – K12 – Ball Valves; K2 – Vacuum Valve, MN – Oil Heater; ВV– Back Valve; F1, F2 – Fine Filter; М1, М2, М3– Manometers; ТP – Temperature Sensor; ТS – Thermostat; RF – Flow relay; EV1- EV6 – Electromagnetic Valves; VG1 , VG2 – Vacuum Relay; L1 – L4– Level Sensors; VP1, VP2 – Vacuum Pumps; РF – Mesh Filter; R – Oil Trap, RP– Pressure Relay
OPERATIONAL PRINCIPLEThe unit can be operated in the following modes:
- oil heating and filtration
- filtration, heating and thermo-vacuum oil purification
- vacuummising of a transformer tank
Name of parameter
|1 Productivity, m3/h, minimum|
|– in thermo-vacuum dehydration and filtration mode||
|– in heating and filtration mode||
|2* Processed oil parameters :|
|– maximum gas content, %, max.||
|– maximum moisture content, ppm, after 3 passes||
|3 Maximum oil outlet temperature in heating mode , ºС||
|4 Outlet pressure, MPa||
|5 Oil heater power, kWt, max.||
|6 Maximum power consumption, kWt, max.||
|7 Electric parameters,|
|– voltage, V||
|– AC frequency, Hz||
|8 Dimensions СММ-1/6, mm,|
|9 Weight, kg||
3D DIAGRAM and PICTURES
1 – Vacuum Chamber; 2 – Inlet Oil Pump ; 3 – Outlet Oil Pump; 4 – Pipes and Connections; 5 – Oil Heater; 6 – Fine Filter; 7 – Vacuum Pump; 8 – Vacuum Booster
GlobeCore Mobile High Vacuum Degasifier CMM-1/6